With the increased focus on fire door assemblies, particularly in health care facilities, I’m receiving numerous questions on this topic. The most recent, received from a fire door assembly inspector, is…
Which door openings are required to have gasketing, according to NFPA 101 – The Life Safety Code?
Since the Centers for Medicare and Medicaid Services (CMS) have adopted the 2012 edition of NFPA 101, that’s the edition I referred to in order to answer this question. [UPDATE: Someone asked me about the 2015 edition of NFPA 101 so I checked that edition and the requirements are the same as below.] I have previously written articles addressing the requirements of the 2009 International Building Code (IBC) as well as the 2015 edition, so if the IBC is the applicable code, refer to those articles.
Similar to the IBC, NFPA 101 does not specifically mandate gasketing for fire doors or smoke doors. Instead, these model codes require some doors to limit the amount of air infiltration to a certain level (3.0 cubic feet/minute/square foot of door opening at 0.10 in. water column for both the ambient and elevated temperature tests) when tested in accordance with UL 1784 – Standard for Air Leakage Tests for Door Assemblies. That’s a mouthful, but the key is to start by looking for a reference to UL 1784.
The 2012 and 2015 editions of NFPA 101 refer to UL 1784 in Section 126.96.36.199, stating that where door assemblies are required by other sections of the code to be smoke leakage-rated in accordance with section 188.8.131.52, they are required to limit the air infiltration to the level stated above, when tested in accordance with UL 1784. This section also requires these door assemblies to be installed in accordance with NFPA 105 – Standard for Smoke Door Assemblies and Other Opening Protectives, and for the assemblies to be inspected at least annually.
The next step is to look in other sections of the code for references to Section 184.108.40.206 and smoke-leakage-rated assemblies.
I found only two references in the 2012 and 2015 editions of NFPA 101 that would require smoke leakage-rated assemblies in accordance with Section 220.127.116.11:
18.104.22.168.4.1 – New fire door assemblies serving an area of refuge shall be smoke leakage-rated in accordance with 22.214.171.124.
126.96.36.199 – Where required by Chapters 11 through 43, doors in smoke barriers that are required to be smoke leakage–rated shall comply with the requirements of 188.8.131.52.
However, I didn’t find any occupancy chapters which currently require doors in smoke barriers to be smoke leakage-rated, so that brings us back to one location – new fire door assemblies serving an area of refuge would require gasketing in order to limit the air infiltration to the level stated in the code.
Annex A of NFPA 101 further clarifies that “Gasketing of doors should not be necessary to achieve resistance to the passage of smoke if the door is relatively tight-fitting.” This language (or similar) appears in sections A.184.108.40.206.1/A.220.127.116.11.1 in reference to corridor doors in new and existing health care facilities, in addition to section A.18.104.22.168 in reference to fire door assemblies. But read on…there’s more.
What about NFPA 80 and NFPA 105? NFPA 80 does not reference UL 1784, but states in Annex A, paragraph A.9.3, “Where door assemblies are used for smoke or draft control, gasketing or reduced clearances might be necessary,” referencing NFPA 105. Although NFPA 105 does require smoke door assemblies to limit the airflow to the stated level when tested in accordance with UL 1784, we need to go back to NFPA 101 and look for locations that are required to be smoke doors installed in accordance with NFPA 105.
Searching NFPA 101 for references to NFPA 105, I found 3 more locations where doors are required to limit air infiltration to the stated level when tested in accordance with UL 1784:
- New door assemblies opening into a vestibule (if provided) that are part of a smokeproof enclosure (22.214.171.124)
- New door assemblies in horizontal exits (126.96.36.199.9)
- Elevator lobby doors in occupant evacuation elevator shaft systems (2012: 188.8.131.52, 2015: 184.108.40.206)
The bottom line is that there are actually very few locations where NFPA 101 requires doors to have smoke gasketing – new fire door assemblies serving an area of refuge, new door assemblies in the vestibule of a smokeproof enclosure, new door assemblies in horizontal exits, and elevator lobby doors in occupant evacuation elevator shaft systems. If anyone finds additional locations or references, please let me know.
Note: If the building was built in accordance with the IBC and doors were required to have gasketing in order to limit air infiltration when tested in accordance with UL 1784, this gasketing should be present and intact when the fire door inspection is conducted. The 2015 edition of the IBC requires limited air infiltration and references UL 1784 for the following locations: elevator lobby doors, doors in smoke barriers in underground buildings and I-3 occupancies (i.e. correctional centers, detention centers, jails, prerelease centers, prisons, and reformatories), and fire door assemblies in corridors and smoke barriers. Refer to this article for more information.