View Larger Image FF: Doggie Door? 15 Comments ⬇ Guess what this is for. And once you figure it out, what do you think about the potential impact on free egress? This is a required means of egress and there is an exit sign (it’s not a fire door). You need to login or register to bookmark/favorite this content. By Lori Greene|2017-10-06T10:19:10-04:00October 6th, 2017|Fixed-it Friday, Means of Egress, Panic Hardware|15 Comments Share This Story, Choose Your Platform! FacebookTwitterLinkedInRedditWhatsappGoogle+TumblrPinterestEmail About the Author: Lori Greene Recent Posts 15 Comments Bob Caron October 6, 2017 at 6:59 am - Reply Since it’s Fix-it-Friday and you are implying that it will have an impact on free egress, it has to be a crazy idea. The little door is so that they can run a water hose from one side to the other without having to leave the big door open. At first I thought that maybe there was no trim or cylinder on the pull side and if you had to get in, you can open the little door and reach up to push the exit device pad. Dave Matas October 6, 2017 at 11:00 am - Reply It’s a “Hose” door. cda October 6, 2017 at 1:55 pm - Reply Dang Smart group !! I had to ask Lee Francisco October 6, 2017 at 3:14 pm - Reply Isn’t that going to be an ADA issue? Lori October 9, 2017 at 11:11 am - Reply Yes it is! – Lori Fred Collier October 6, 2017 at 3:15 pm - Reply Positive Pressure / Negative Pressure release Daniel Poehler October 6, 2017 at 4:11 pm - Reply It’s a built-in mail box for a key, a lockbox that’s built in to the door. Daniel Poehler October 6, 2017 at 4:32 pm - Reply Lori, Picture a 2 story restaurant with an outdoor second floor dining area. The area has over 50 occupants, one exterior stair and an egress door back into the interior leading to another stair. This door requires a panic device, so how do I provide security after hours to an inward swinging door with a panic device that could potentially be an entry point for a robber? I don’t know how to email you other than the blog replies, so I apologize if my question has gone through an improper channel. Thanks… Lori October 9, 2017 at 11:24 am - Reply Hi Dan – You can email me at firstname.lastname@example.org and sometimes I’ll be able to see and respond to the question more quickly. It’s not easy being a one-woman show! 🙂 Because the restaurant has more than 50 occupants, you need 2 means of egress. This means that the door back into the building must meet the requirements for an egress door. Technically, the panic hardware is required and the door must allow free egress (and therefore access to the building) at all times, but I understand the problem. If the occupant load of the restaurant is 300 people or less, one possibility is to use a key-operated lock as allowed by the IBC (see below) instead of panic hardware. Approval should be requested from the AHJ because this section is typically applied to the main door of the building, not the main door of a space within the building. 1010.1.9.3 Locks and latches. Locks and latches shall be permitted to prevent operation of doors where any of the following exist: … 2. In buildings in occupancy Group A having an occupant load of 300 or less, Groups B, F, M and S, and in places of religious worship, the main door or doors are permitted to be equipped with key-operated locking devices from the egress side provided: 2.1. The locking device is readily distinguishable as locked. 2.2. A readily visible durable sign is posted on the egress side on or adjacent to the door stating: THIS DOOR TO REMAIN UNLOCKED WHEN THIS SPACE IS OCCUPIED. The sign shall be in letters 1 inch (25 mm) high on a contrasting background. 2.3. The use of the key-operated locking device is revokable by the building official for due cause. … – Lori Joel Niemi October 6, 2017 at 6:43 pm - Reply doggie door for a pet python? Anthony Wan October 6, 2017 at 7:02 pm - Reply Could be a door for the charging cable for a plug in electric car. Deanne October 7, 2017 at 8:01 am - Reply It’s at Geico headquarters, for the little gecko to go in and out. Kent Usher October 8, 2017 at 6:07 pm - Reply Does not comply with ICC A117.1 404.2.9. Marco Merchiori October 9, 2017 at 8:29 am - Reply I am guessing it is a door to allow a line to be brought without leaving the door open. Again which would impede the opening of the door. Holly Brisby-King October 10, 2017 at 9:44 pm - Reply Wow, just wow!!! What people will do to exit doors!! I’m agreeing with the hose access… Leave A Comment Cancel replyComment Save my name, email, and website in this browser for the next time I comment. Don't subscribe All Replies to my comments Notify me of followup comments via e-mail. You can also subscribe without commenting.